Atmospheric Corrosion Atmospheric corrosion is an abnormal operating condition that is characterized into four levels. Levels one and two will not result in a disapproved Local Law 152 inspection; however, if the corrosion is not properly addressed in a timely manner, the repercussions will be costly repairs and prolonged gas shutdowns in your building. As […]
Gas leaks are one of the most hazardous abnormal operating conditions, and they present an immediate danger when they occur. Many different reasons can bring about a gas leak. Improper installations, atmospheric corrosion, inadequately supported piping, and failure to protect the pipes from physical impacts are some of the abnormal operating conditions that can eventually
Abnormal Operating Conditions (AOC) Discovering any abnormal operating conditions will prevent a building from passing a Local Law 152 inspection. Abnormal operating conditions are potentially unsafe conditions in the piping, such as gas leaks, non-compliant installations, atmospheric corrosion, theft of service, and diversion of service. If discovered during the inspection, there are certain conditions that pose an
We are incredibly proud to announce that C.C. Controlled Combustion Co. Inc. to be partners with Spectrum Designs to provide uniforms and a variety of swag for our employees. This includes not only our team T-shirts and ballcaps but also a wide variety of other items. This all started a little over a year ago
A tightness test is a means of determining whether a storage tank and/or its piping system are leaking. DEC requires using a test that can detect a tank or piping leak of 0.1 gallons per hour (gph) (with a probability of at least 95% and no more than 5% probability of false alarm. The test
C.C. Controlled Combustion Co donates to support The General Society of Mechanics and Tradesmen. Enriching the lives of the students that enroll.
Multifamily Energy Efficiency Program: Gas Incentives Multifamily Energy Efficiency Program: Electric Incentives CC Controlled Combustion is a Participating Contractor with Con Edison’s Multi-Family Energy Efficiency Program, which incentivizes multi-family buildings that are FIRM GAS Con Edison customers to install Energy Management Systems, boiler equipment upgrades, advanced boiler cleaning & tuning, & boiler room pipe insulation.
COVID-19 Restrictions and Preparations During these uncertain times of unprecedented restrictions on amenities and supplies due to the Coronavirus Pandemic, it is impossible to know what is going to happen next. Presently there have not been restrictions placed on Commercial Heating/HVAC contractors nor have we had any reported cases of COVID-19 but new restrictions and
The Controlled Combustion Team would like to give a special thanks to all the sponsors that helped make our Employee Appreciation Event possible. Last night February 21, 2020 employees were treated to a night out at Madison Square Garden for a New York Knicks game. The owners of Controlled Combustion with the help of its
On January 13th at 5am a 3-foot water main broke sending over 500,000 gallons of water rushing down Broadway and turning the streets between West 61st and West 65th into a river. NYC & Con Ed Crews worked for over 3 hours to shut off the water but by that time many of the local